On 11/08/2016 11:33 AM, Guy Sotomayor Jr wrote:
Yea, that?s what I?m struggling with. The issue is
the control units power the devices that are connected to
them (from what I can tell), so I have to power the entire
string as one unit. The same goes for the 3340?s - the
entire string is powered as a unit. The string of 3340?s
need ~5kVA (I don?t know how that translates to HP). I?m
still trying to figure out the requirements for the other
strings. TTFN - Guy
Just a warning, you MUST NOT power electronics from a VFD!
(In theory, you can do it with a VERY effective filter, but
I've never heard of anybody having success with it.) They
produce high frequency square waves at 400 V, and will do
great damage to electronic loads. They work great for
motors, although the HF square waves can cause noise issues
in sensitive electronics like tape and disk drives.