Pleas ID this IBM system....
cc at informatik.uni-stuttgart.de
Wed May 22 02:49:59 CDT 2019
On Tue, 21 May 2019, Patrick Finnegan wrote:
> Plumbing (unless you're doing aisle containment or RDHx) shouldn't run
> through the IT space in the data center.
So how exactly do you attach a modern water cooled rack system to your
cooling water system if not using plumbing?
> Cooling water to racks should be dewpoint adjusted, so you don't need
> condensate drains inside the DC.
That is a requirement, you must have condensate drains just in case that
the room temperature and/or air humidity rises, or cooling water
temperature goes below the dew point.
More information about the cctalk